AX Wall Exhaust Fan Variable Speed 16 inch 2570 CFM Direct Drive AX16-1V
The product Build Time you see represented on this site is only a typical number of days the manufacturer states it needs to build the product(s) when ordered. Build times are based on business days (excludes weekends & holidays).
The build time does not include the time it will take to ship the order to you (the customer). If an order has multiple items and comes from multiple warehouses, you may receive part of your order on one day, and then receive the remaining part(s) of your order at a later date.
*Please be aware that seasonal demand of certain equipment may cause build times to run longer than what is typical.
|Quantity||Unit Price||You Save|
The Canarm AX series exhaust fans are a sturdily constructed, direct drive, horizontal discharge fan that is typically used for general ventilation of factories, garages, warehouses and other industrial or commercial buildings. The AX fans are available in multiple single-speed variations as well as two-speed and variable speed models. The AX series housings are constructed of heavy duty aluminum with built in shutters that automatically open when the fan starts and gravity closes when the fan stops.
*INSIDE WALL INSTALLATIONFeatures:
Sturdily constructed from all-aluminum extrusions.
8” - 24” models have heavy wire chrome plated
OSHA guards on intake side of fan.
30”, 36” & 42” models have grey powder coated guards.
Totally enclosed air over motor with overload products.
The shutter mounted direct drive exhaust fan installs on inside wall.
It eliminates need for external framing and shutter.
*NOTE: The motor Full Load Amperage ratings are meant to be used as a General guideline only. The ratings are from the primary motor supplier. These amperage ratings may vary slightly if a different motor supplier is used. It is also possible that a motor manufacture may modify / improve / update a motor in which the amperage rating will change slightly.
a = 20-3/4 in.
b = 17-3/4 in
c = 5 in.
d = 11 in. (approximation dependent on motor manufacturer)
- Model No.:
- AX16 -1V
- 115 / 230
- New York
- Exhaust Fans
- Blade Material:
- Blade Size (Inches):
- No. of Blades:
- CFM High:
- Decibels (dBA):
- 68 @ 5ft
- Dimension Inches:
- Width: 20.75" Depth: 16" Height: 20.75"
- Drive Type:
- Limited Warranty:
- 1 Year Limited
- RPM High:
- Weight lbs.:
Notice: Manufacturer's products features and specifications are subject to change without notice.
California Residents: WARNING- This product may contain chemicals known to the State of California to cause cancer and birth defects or other reproductive harm. For more information, please visit www.P65Warnings.ca.gov.
QUESTIONS & ANSWERSAsk a Question
In the product details it appears the rough wall opening needs to be 17.75" sq, but in the specs its states its is 20.75" sq. Also , it states EF mounts on inside wall. Here is what I have, please indicate which fan will fit the best. I am replacing an existing louvered exhaust fan. The existing wall opening is 20.75" sq. The wall is an 8" block wall with brick veneer, so about 12" thick. I want the new fan shutters to completely cover the hole on the outside of the wall. Inside of the wall does not matter, because it is an equipment room. I would prefer to just remove the old entire fan/shutter assembly, and slide the new fan thru the hole from the outside and screw it off into the brick. Please recommend which of you products will do this. I can frame the inside of the rough opening with 1x12, or 2x12, if necessary leaving a rough opening of 19.25" or or 17.75 respectively, if required. Please advise. Thanks You may call me at 865-679-2205 if this would be easier to discuss by phone.
Thank you for your question. Here is a link to the manufacturers spec sheet on for the fan. It appears as though the shuttered, outward facing dimension of the fan housing is 17 3/4", and the mounting flange is 20 3/4". The installation guide (also linked below), says that you should be 1/2" larger than the shutter box size (allowing 1/4" on all sides for clearance). These fans are meant to be installed from the inside of the building, with the flange on the interior side of the hole.
Install - https://cdn.shopify.com/s/files/1/0972/5538/files/AX_Manual.pdf?12965407212672133746
Specs - https://cdn.shopify.com/s/files/1/0972/5538/files/AX_Series_Literature_c8053f8e-4902-4c38-9a58-308d86b72e22.pdf?v=1599075213
Can we install this for kitchen?
This wall exhaust fan can be used in kitchens for the purpose of general exhausting. This fan should not be used for high heat from stoves, or steam.