SD Exhaust Fan w/ Shutters 1 Speed 16 inch 2370 CFM Direct Drive S16-E1
The product Build Time you see represented on this site is only a typical number of days the manufacturer states it needs to build the product(s) when ordered. Build times are based on business days (excludes weekends & holidays).
The build time does not include the time it will take to ship the order to you (the customer). If an order has multiple items and comes from multiple warehouses, you may receive part of your order on one day, and then receive the remaining part(s) of your order at a later date.
*Please be aware that seasonal demand of certain equipment may cause build times to run longer than what is typical.
|Quantity||Unit Price||You Save|
Canarm / LFI’s standard fans follow a tradition of quality in design, materials and construction. All our standard fans are developed to be efficient and economically priced. Fans are available in single, two and variable speed models. All variable speed standard fans use an energy efficient variable speed, dual voltage motor and blade combination.
Inside wall installation
Available in 8” to 42” sizes.
Single, two and variable speed models are available.
All fans use a totally enclosed, thermally protected motor.
The rugged steel welded box housing has a durable powder coated finish.
Aluminum louver shutters are supported by long life nylon bushings
(30”, 36” & 42” have PVC louvers).
8” - 24” models have heavy wire chrome plated OSHA guards on intake side of fan.
30”, 36” & 42” models have grey powder coated guards.
All fans are shipped completely assembled.
A = 21-1/4"
B = 17"
C = 6"
D (center to center) = 20"
E = 18-3/4"
N = 4
- Model No.:
- S16 -E1
- New York
- Exhaust Fans
- Blade Material:
- Heavy-Gauge Aluminum
- Blade Size (Inches):
- No. of Blades:
- CFM Low:
- CFM High:
- Decibels (dBA):
- 66 @ 5ft
- Dimension Inches:
- Width: 21-1/4" Depth: 6" Height: 21-1/4"
- Drive Type:
- Limited Warranty:
- 1 Year Limited
- Motor Type:
- RPM High:
- Weight lbs.:
Notice: Manufacturer's products features and specifications are subject to change without notice.
California Residents: WARNING- This product may contain chemicals known to the State of California to cause cancer and birth defects or other reproductive harm. For more information, please visit www.P65Warnings.ca.gov.
QUESTIONS & ANSWERSAsk a Question
We are looking for several 16” fans to be used within a wood kiln operating continuously at about 120 degrees. Will the S16-E1 work in these conditions?
No. THis fan is only rated for 104 deg. F, as is most fans. This unit (V4E40K2M71100) 16" exhasut fan will work in temps up to 140 deg. F.
Looking at the fan what way does he fan turn to exhaust the building? I bought this fan & did not realize it was dual voltage.
If you are facing the blade side of the fan, the blade should be roataing clock-wise when on. This is for exhaust or pulling the air out of the room or space..
Does this come with a remote?
This fan does not come with a remote control, not is it a remote controlled fan.
We have a 12 inch square opening in our building for an exhaust fan what size do I need
The AX10-3 wall exhaust fan should filt within this opening.
Can you use this on a commercial vent hood?
This Canarm brand exhaust fan is a high quality fan that has many commercial applications.
I need a fan size of 20 “ x12 “ is this possible
No. Typically a wall mounted exhaust fan is square and not rectangular.
Does this have the powered louvers
This fan has gravity louvers, not motorized.
We want to install this in our food truck. Will it stay on if it gets really hot up in the hood? What size do you recommend. Our truck is 21’x8’. How much room is required up in the hood to fit this unit.
You will want to contact us directly regarding the fan needed. Call 866.727.1060
Is this fan explosion proof I was considering it for a 14 by 24 by 8 foot paint booth
This fan is NOT explosion proof. You will want to look at the AX14-4 or the SD18-XPF
what size wall shutter fan is required for a garage 50 ft wide x 50 ft long x 18ft high
You have a total of 45,000 cubic feet of air in this space. 6500 CFM would exchange the air approx. one time per 7 minutes, which is fairly typical for your application. You may want to look at two fans doing roughly 3500 CFM each.
My building is 36x64 with a 16 foot sidewall is this fan big enough to exhaust my space?
The cubic feet of your area is approx. 37,000. This fan would only exchange the air in your building approx. once every 15 to 17 minutes. It is typically suggested to exchange the air in a warehouse type buildiing once every 7 minutes or less. This would require approx. 5,300 CFM.
Is the motor brushless?
Yes. The motor on this fan is brushless. This is a PSC type motor.